# How Do I Calculate Voltage Drop?

January 1, 2006

Q: I have a barn on my property that I would like to get power to. This barn is 377 feet from the nearest power. I would like to have 50 amps @240 volts and I’m going to run my power in conduit. What size wire do I need to run?

A: The formula for voltage drop is: Vd = 2K x L x I / Cm

Vd = Voltage Drop
I = Current in Conductor (Amperes)
L = One way Length of Circuit
Cm = Cross Section Area of Conductor (Circular Mils)
K = Resistance in ohms of one circular mil foot of conductor
K = 12.9 for Copper Conductors @ 75 degrees C
K = 21.2 for Aluminum Conductors @ 75 degree C
/ = Divided by

I will assume you are going to use copper conductors and your temperature is @ 75 degrees C.

Reasonable operating efficiency is achieved if the voltage drop of a feeder or a branch circuit is limited to 3 percent. However, the total voltage drop of a branch circuit plus a feeder can reach 5% and still achieve reasonable operating efficieny (210.19(A)(1)FPN No. 4 or 215.2(A)(4)FPN No. 2).

8 AWG = 50 amps @ 75 degrees C = 16510 Cm
Vd = 2 x 12.9 x 377 x 50 / 16510 = 30 volts
30 volts / 240 volts = 0.125 = 12.5% = Not Acceptable

6 AWG = 65 amps @ 75 degrees C = 26240 Cm
Vd = 2 x 12.9 x 377 x 50 / 26240 = 19 volts
19 volts / 240 volts = 0.079 = 7.9% = Not Acceptable

4 AWG = 85 amps @ 75 degrees C = 41740 Cm
Vd = 2 x 12.9 x 377 x 50 / 41740 = 12 volts
12 volts / 240 volts = 0.05 = 5% = Not Acceptable – This is not acceptable because the 5% voltage drop is at your sub panel. If you were to run any wire beyond the sub panel, your voltage drop would exceed 5%. I’m assuming you are going to install a light and some receptacles in your barn.

3 AWG = 100 amps @ 75 degrees C = 52620 Cm
Vd = 2 x 12.9 x 377 x 50 / 52620 = 9 volts
9 volts / 240 volts = 0.038 = 3.8% = Acceptable

Your equipment grounding conductor (ground wire) is sized off of table 250.122. You need to run a 10 AWG copper ground wire for this circuit.

To summarize; you need to run 3 – 3 AWG (2-hots and 1-neutral) branch circuit conductors and 1 – 10 AWG equipment grounding conductor (ground wire).

Tip: The rule of thumb is to plan for voltage drop at 100 feet and increase one wire size for every 100 feet thereafter.

Happy New Year!

Do you need assistance with your electrical wiring project? Please visit my DIY Electrical Wiring Help from a Master Electrician page. Where I provide electrical wiring tips, expert electrical advice, answers to your electrical questions and electrical consulting & design services over the phone, via instant messenger or via email.

Similar Posts:

2 Responses to “How Do I Calculate Voltage Drop?”

1. ken. Good on November 23rd, 2008 11:06 am

I have 220 volt- 30 amp heater. What are the safe breakers in the panel?
I had 2×15 but they are trippping periodically. Would 2×30 be too heavy ?

2. Ahmed Kadhem on January 3rd, 2009 5:13 am

According to NEC 2008 Chapter 9 , table 8 , that we can get cross section area of conductor (circular mils) from 18 AWG to 4/0 AWG what the cross section area of conductor (circular mils) 250 AWG

Please solve the following simple math problem so that we know you are a real person * Time limit is exhausted. Please reload CAPTCHA.