Connecting 2 Ground Rods To Your Service
January 3, 2006
Q: Can I connect two ground rods spaced about 6 feet apart directly to the service equipment disconnect or should I run the ground wire from one rod to the other then to the service equipment disconnect?
A: The 6 AWG copper grounding-electrode conductor may be run from one rod to the other in an unbroken length, then to the neutral bus in the service disconnect. The grounding-electrode conductor is required to be unbroken in one continuous length or may be spliced by irreversible compression-type connectors or exothermic welding. This requirement appears in 250.62(C). Individual 6 AWG-copper conductors may also be run from each ground rod to the service disconnect; however, individual terminals in the service disconnect must be provided to terminate the two 6 AWG grounding-electrode conductors. This arrangement is permitted by 250.64(F).
Do you have an electrical question you would like us to answer? We will answer the first question posted to this blog daily. Your answer will be posted in the next day’s blog. If you need your question answered sooner, visit www.gilchrist-electric.com
Do you need assistance with your electrical wiring project? Please visit my DIY Electrical Wiring Help from a Master Electrician page. Where I provide electrical wiring tips, expert electrical advice, answers to your electrical questions and electrical consulting & design services over the phone, via instant messenger or via email.