Using The GFCI Receptacle In An Unfinished Basement To Feed A Washing Machine
March 29, 2006
Q: Is it permissible to use the GFCI receptacle in an unfinished basement of a one family home to provide power to a washing machine and gas clothes dryer?
A: If this is the only receptacle in the basement, the answer is no. A receptacle protected by a GFCI is required by 210.8(A)(5), and 210.52(G) requires at least one receptacle outlet in addition to any provided for laundry equipment. The receptacle(s) for the laundry equipment may be supplied by the same branch circuit that supplies the GFCI receptacle. The receptacle(s) for the washer and dryer may be connected to the line side of the GFCI protected receptacle as allowed by Exception 2 of 210.8(A)(5) or may be connected to the load side of the GFCI receptacle or to the GFCI circuit breaker that supplies the basement receptacle.
Do you have an electrical question you would like us to answer? We will answer the first question posted to this blog daily. Your answer will be posted in the next day’s blog. If you need your question answered sooner, visit www.gilchrist-electric.com
Do you need assistance with your electrical wiring project? Please visit my DIY Electrical Wiring Help from a Master Electrician page. Where I provide electrical wiring tips, expert electrical advice, answers to your electrical questions and electrical consulting & design services over the phone, via instant messenger or via email.
- Can I Install The Required Light And Receptacle On The Same Circuit As The Furnace?
- Receptacles in Crawl Spaces and Unfinished Basements
- Finding Bolts for Your Electric Dryer Power Cord, Wiring a 3-Prong Dryer Receptacle and Wiring GFCI Receptacles
- Receptacle Spacing In Single Family Dwelling Units
- Wiring An Electric Water Heater