Wiring a Motion Sensor Light, Installing an Electric Baseboard Heater in a Closet and Grounding Your Electric Dryer
February 14, 2009
James Vida asks:
I’ve got 3 wires coming from a light sensor (red, black & white) and 2 wires + ground that come from my light. I know that I connect white-to-white and black-to-black, gnd-to-gnd; where does the red wire connect?
You should have 1 more cable with 3 wires in it which come from the switch or power source. The first thing that you need to do is determine which wire is the line and which is the load from your light sensor. After that ensure that the power is off and check it at the light with a voltage meter before beginning work.
Now connect all of the ground wires together, place a wire nut on them and tuck them into the box. Next connect all of the neutral wires together, place a wire nut on them and tuck them into the box. Now connect the black wire coming from the light to the load side of the light sensor. Next connect the black wire coming from the light switch or power source to the line side of the light sensor. Finally, install the light, turn on the power and test.
Joseph Casha asks:
I want to add a 3ft hydronic electric heater to an existing 2ft heater and use the same thermostat. The 2ft heater is in the bathroom and the additional heater with be located in a closet which is directly opposite the bathroom is there a specific wiring configuration I need to use. If so,can you give me a heads up on the correct wiring? Both heaters are 240volts.
I do not recommend this. The National Electrical Code® (NEC®) does not specifically restrict fixed electric space heaters from being installed in a closet, but NEC® section 424.13 states “Fixed electric space-heating equipment shall be installed to provide the required spacing between the equipment and adjacent combustible material, unless it is listed to be installed in direct contact with combustible material.”
It is also not recommended to control an electric baseboard heater from a thermostat in another room. The thermostat in the other room will not accurately detect the temperature in the opposite room with your new heater.
I’ve just changed the cord to my dryer but the green ground bolt is at quite a distance from the black, white and red hookups and the green cord won’t reach that far. I’ve grounded it to another screw and the frame of the dryer but I’m not certain that’s good enough?
In theory, this will work. However, I recommend connecting the ground wire to the green ground screw provide by the manufacturer. To lengthen the wire, simply strip a little more off of the outer sheath of the cable and push the cable further into the dryer’s wiring compartment.
Do you need assistance with your electrical wiring project? Please visit my DIY Electrical Wiring Help from a Master Electrician page. Where I provide electrical wiring tips, expert electrical advice, answers to your electrical questions and electrical consulting & design services over the phone, via instant messenger or via email.
- How To Turn Off an Electric Baseboard Heater That Stays On All of the Time, Wiring a Heater with 4 Wires and Wiring a Motion Sensor Light
- Answers To Electrical Questions About GFCI Wiring, Wiring A Thermostat and Converting A Bandsaw Motor To 220 Volts
- Answers to Electrical Questions About Wiring A New Dryer Power Cord, Wiring 110V Heaters with a Double Pole T-Stat, and Troubleshooting 105 Volts Between the Dryer and Faucet.
- Answers To Electrical Questions About Ampacity Rating For #4 SER Cable, Installing A Ceiling Fan In A Kitchen And Wiring A 2 Bulb Sensor Light
- Answers to Electrical Questions About Wire Size in a Bedroom, Wiring a Switch Loop and Wiring a 3-way Switch