Installing Romex Through Metal Studs
April 9, 2006
Q: Does the NEC allow romex to be run though metal studs that are provided with a threaded bushing and held in place by a locknut?
A: There are two Code references that apply to this installation. They are 300.4(B)(1) and 334.17. Where nonmetallic-sheathed cable is pulled through slots or holes in metal framing members, the cable must be protected by listed bushings or listed grommets that are securely fastened to the framing members prior to installation of the cable. This requirement is more restrictive in 334.17 because the grommets or bushings must be listed for protection of the cable.
If the threaded bushing that is held in place by a locknut is listed for the purpose of cable protection, it meets the requirements in the National Electrical Code.
Do you have an electrical question you would like us to answer? We will answer the first question posted to this blog daily. Your answer will be posted in the next day’s blog. If you need your question answered sooner, visit http://www.gilchrist-electric.com/
Do you need assistance with your electrical wiring project? Please visit my DIY Electrical Wiring Help from a Master Electrician page. Where I provide electrical wiring tips, expert electrical advice, answers to your electrical questions and electrical consulting & design services over the phone, via instant messenger or via email.
- Answers to Electrical Questions About Wiring in Metal Studs, Rewiring Pendant Fixtures, Switches for Garbage Disposals and Rewiring Kitchen Lights
- Room Air Conditioner Requirements
- Is It Necessary To Ground Dimmer Switches?
- Installing Romex In A 2 Inch Metal Conduit Into A Panel
- Installing Boxes For Wall Mounted Light Fixtures