Answers to Electrical Questions About Wiring a Ceiling Fan, Disconnecting a Receptacle in a Staircase and Wiring a Tanning Bed
January 24, 2011
I have installed a ceiling fan and light in my living room. I have a three way switch that controls one receptacle that I have a lamp plugged into that gives me light in the living room. One light switch turns the lamp on when you enter the house and the other one turns it off when you go in the kitchen. I can turn the lamp on or off from either side of the room. I need help getting power to the fan and light. Can you help me get my fan and light to work?
Yes I can make this work, but I need more information. Do you already have a light box in the ceiling where you plan to install the fan/light? I believe that your best solution is hire me to walk you through the process. Please visit my DIY Electrical Wiring Help from a Licensed Master Electrician. I recommend option #2.
Here is a general overview of what needs to be done to make this happen. I’m going to assume that there is no light box or power to the location where you plan to install your fan/light. First, you need to determine which switch box has the power supply in it. Now I would remove this switch box and enlarge the opening to install a larger switch box which will accommodate 2 more switches (1 to control the fan and 1 to control the light). Then install a 3 conductor cable with ground from this box to your new fan/light box in the ceiling. At the ceiling location, you need to securely install a “fan rated” box. You can’t use just any light box for a paddle fan as it will eventually fail and your fan will come crashing down onto someone.
Now hang the fan and connect the wires. Connect the green wire from the fan to the bare copper wire in the 3-conductor cable with ground. Connect the white wire from the fan to the white wire in the 3-conductor cable with ground. Connect the black wire from the fan to the black wire in the 3-conductor cable with ground. Connect the blue wire from the fan to the red wire in the 3-conductor cable with ground.
Now go to your new switch box, make the terminations, install the switches and cover plate.
I would like to know if a hot electric outlet found in the staircase wall can be disconnected and if so how much would if cost? Average price please.
Yes it can be disconnected. I would charge you a maximum of $34.95 for my service. Please visit DIY Electrical Wiring Help from a Licensed Master Electrician. I recommend option #2.
To disconnect this properly, you need to trace the cable which supplies power to this receptacle back to the source and disconnect it there. This is probably fed from a nearby receptacle or light switch box. I can walk you through this process.
I just purchased a tanning bed and the problem that I am having is I was told it would run on the same outlet as my dryer….well, not true. Both cords are 3 prong but the one on the tanning bed is a different type of 3 prong. What can I do to fix this problem, or better yet what would be the easiest & safest way to solve it without having to hire an electrician. I live in an apartment and the landlord is OK with the tanning bed as long as I don’t have to have BIG electrical work done. Any and all help would be great…I would like to be tan before summer but want to do it the safe way…..lol Thanks!!!!
I really need more information to help you solve this issue. I need the power requirements from your tanning bed. I also need the NEMA configuration marked on your power cord. It should be something like 6-30P or 14-30P. Again, I think you would be best served by visiting my DIY Electrical Wiring Help from a Licensed Master Electrician page.
Do you need assistance with your electrical wiring project? Please visit my DIY Electrical Wiring Help from a Master Electrician page. Where I provide electrical wiring tips, expert electrical advice, answers to your electrical questions and electrical consulting & design services over the phone, via instant messenger or via email.
- Q&A About Wiring a Tanning Bed, Installing a GFI Receptacle on a Non-Grounded Circuit, Wire Size for a 100 Amp Sub Panel and Troubleshooting an Electric Baseboard Heater
- Installing 3-way Switches to Control a Ceiling Fan and Light Independently
- Adding Electric Baseboard Heaters to an Existing Circuit, Wiring Four Light Switches and Changing Light Switching Around
- Answers to Electrical Questions About Wire Size in a Bedroom, Wiring a Switch Loop and Wiring a 3-way Switch
- Answers to Electrical Questions About Lighting Circuits and Dryers