How to Wire a Recreation Room in Your Basement – Part 1: Creating a Materials List, Installing the Boxes, Recessed Cans and Exhaust Fan
March 21, 2008
Congratulations to Brian Roth on winning my February contest “Complete Your Next DIY Electrical Wiring Project with Help from a Master Electrician for Free“.
Brian emailed me a pdf document of his basement and what he wants. So, today’s article will discuss a materials list and installing the boxes, recessed cans and exhaust fan phase of this project. I will write a second part to this article tomorrow covering installing all of the cables.
So, let’s start with a materials list. You need:
21 – Single gang nail on boxes
5 – Two gang nail on boxes
7 – 4 inch round nail on boxes
3 – Low voltage boxes
11 – Recessed cans
1 – Exhaust fan
1,500 feet – 12/2 with ground NM cable (romex) (approximately)
200 feet – 14 AWG speaker wire (approximately)
RG-6 quad shield coaxial cable
Category 5 (CAT5) phone and data cable
1,000 – Plastic romex staples (approximately)
Green wirenuts or crimp connectors
2 – In ceiling speaker brackets
4 – In wall speaker brackets
I didn’t provide cable lengths for the RG-6 coaxial cable or the CAT5 phone and data cable because I don’t know where they need to end up. Each location should be an individual “home run” back to the main location. I will discuss this more in part 2 of this series.
Alright, now that we have the materials needed for the rough in phase, let’s start nailing up boxes. This first diagram shows the location of all of the single gang boxes indicated by red circles. I typically install my receptacle boxes at 18 inches above the floor to the top of the box. However, I recommend matching the height of your existing receptacles. Switches are typically installed at 48 inches above the floor to the top of the box and counter top receptacles are typically installed at 42 inches above the floor to the bottom of the box. However, I recommend matching the height of your existing receptacles and switches here as well.
Please note that I added a few boxes. There was nothing in the storage area. I recommend installing a light controlled by a switch and a receptacle in the storage area. This is not a National Electrical Code® (NEC®) requirement, but I think you will find this useful in the future. I also added a switch for your undercabinet lights. This is a much better option than just plugging in the lights.
Additionally, I added a smoke detector. You may not need this if there is an existing smoke detector in your basement. However, if there is not an existing smoke detector in your basement, then you need to add this one. You will also need to check with your local building codes department to determine if you need to connect this smoke detector to your existing smoke detector circuit. I highly recommend connecting the added smoke detector to your existing smoke detector circuit; even if your local building code does not require this. However, this could be very challenging to do.
Click this link to supersize the image (95k file size)
|This next diagram shows the location of all of the 2 gang boxes indicated by red circles. Please note that I added 1 – 2 gang box in the bathroom for the switches to control the exhaust fan and lights. I also used 2 – 2 gang boxes at the bottom of the stairs for the switching instead of 1 – 4 gang box. The reason for this is I assumed that you are going to install dimmer switches to control your lighting. Dimmer switches fill the boxes more than regular switches and put off more heat. Using 2 – 2 gang boxes will create a lot less problems than using 1 – 4 gang box when installing dimmer switches.||
Click this link to supersize the image (75k file size)
This diagram shows the location of all of the round boxes indicated by red circles. Please note that I added 1 round box in the storage area for the light. The wall sconces are mounted at all different heights. These really depend on personal preference. Depending upon the type of light fixture you are going to use, I recommend mounting your sconces around 5 – 6 feet above the floor.
The vanity light is typically mounted at 80 inches above the floor to the center of the box. However, this also depends upon the mirror that will be used as well as the type or style of light fixture you plan to install.
Click this link to supersize the image (70k file size)
|With all of the round boxes installed, let’s get started installing the recessed cans and the exhaust fan in the bathroom. The recessed can locations are indicated by red circles. Please note that I recommend moving the exhaust fan in the bathroom.||
Click this link to supersize the image (77k file size)
|Now that all of the recessed cans and exhaust fan are installed, let’s install the low voltage boxes for the phone and TV connections. The locations are indicated on the diagram by red circles||
Click this link to supersize the image (67k file size)
|The final step in this process is to install the speaker mounting brackets. The locations are indicated on the diagram with red circles. The 2 larger circles are ceiling mounted speakers and the smaller circles are in-wall speakers.||
Click this link to supersize the image (71k file size)
|Be sure to check back for part 2 of this series, where we will discuss the installation of the power, audio, phone and video cables.|
Do you need assistance with your electrical wiring project? Please visit my DIY Electrical Wiring Help from a Master Electrician page. Where I provide electrical wiring tips, expert electrical advice, answers to your electrical questions and electrical consulting & design services over the phone, via instant messenger or via email.
- Answers to Electrical Questions About Installing New Lights, Wiring Ceiling Fans and Installing a Receptacle
- Wiring 2 – 1/2 Switched Receptacles Controlled by 3 Switches
- Wiring Diagrams
- What are the Requirements for Installing Smoke Alarms, Heat Detectors and Carbon Monoxide Detectors in Your Area?
- Smoke and CO detectors added to tax-free list