Laundry Room Receptacles
December 3, 2005
Q: Does the NEC permit more than one laundry room receptacle in the laundry area of a one family dwelling unit?
A: Yes, it does. 210.11(c)(2) requires a 20-ampere branch circuit for laundry receptacle outlets. This branch circuit may supply more than one receptacle, but it cannot supply any loads other than receptacles in the laundry. 210.52(5) states “In dwelling units, at least one receptacle outlet shall be installed for the laundry.” The two exceptions do not apply to single family dwelling units.
There is a change in the 2005 NEC that requires GFCI protection for all 15- and 20-ampere, 125-volt receptacles located within six feet of the laundry tub or sink (210.8(A)(7).
Get the Tools and Guidance You Need to SAFELY and Successfully Complete ALL of Your “Do-It-Yourself” Home Wiring & Installation Projects from a Master Electrician with Over 20 Years Experience by visiting www.gilchrist-electric.com today.
Do you need assistance with your electrical wiring project? Please visit my DIY Electrical Wiring Help from a Master Electrician page. Where I provide electrical wiring tips, expert electrical advice, answers to your electrical questions and electrical consulting & design services over the phone, via instant messenger or via email.
- Branch Circuit For Microwave Oven
- Does A Wall Switch In A Bedroom, That Controls Outside Lights, Have To Be AFCI Protected?
- Are Recessed Cans Installed Above Bathtubs Required To Be GFCI Protected?
- How Many Receptacles Are Allowed On A 20 Amp Circuit?
- How many receptacle outlets are required in a large Foyer of a home?