Milbank Manufacturing Recalls Single Meter Sockets Due to Fire and Electrocution Hazards
December 17, 2009
On October 15, 2009 Milbank Manufacturing Co., of Kansas City, MO recalled approximately 1,400 single meter sockets. A short may occur while in use due to an incorrect bridge installed in the product, to which the meter clips are attached. If the manufacturing defect exists, all metal parts of the meter could create a shock or burns can occur if the cover is off and the meter socket is energized. Three incidents have been reported of the unit shorting out. No injuries were reported.
The single meter 200 amp/4 terminal sockets are used for underground utility meter installations. The meter socket is 20 3/4 inches high by 9 inches wide and 4 1/2 inches deep with 1 meter position. It is used by the approving utility to mount their electric meter to measure how much electricity a residence uses. It can be used for an underground residential application. The recalled model number 9090 appears on the right or left side of the installed meter socket. If not installed, model numbers U9090-O or R9090-O will appear on the label on the outside of the box.
These units were sold at electrical supply distributors in N.Y., Pa., Vt. and Mass. and at local hardware stores in N.Y. from May 2009 through August 2009 for about $70. They were manufactured in the United States.
You should stop using the recalled product immediately and contact the electrical supply contractor who installed the sockets. Contractors will contact Milbank Manufacturing for a replacement or reimbursement. Milbank will contact all distributors and stores where the recalled product was sold.
For additional information, contact Milbank Manufacturing’s Sales Engineer toll-free at (888) 537-0881 between the hours of 8 a.m. and 4 p.m. CT Monday through Friday, or visit the company’s Web site at http://www.milbankmfg.com/Recall/RecallForm.aspx
Do you need assistance with your electrical wiring project? Please visit my DIY Electrical Wiring Help from a Master Electrician page. Where I provide electrical wiring tips, expert electrical advice, answers to your electrical questions and electrical consulting & design services over the phone, via instant messenger or via email.
- Amprobe Recalls Clamp Meters Due to Shock Hazard
- General Electric Toasters Recalled by Wal-Mart Due to Fire and Shock Hazards
- Gas Dryers Recalled By General Electric Due To Shock Hazard
- Power Supplies Recalled by RadioShack Due to Electrocution and Fire Hazards
- Harbor Freight Tools Recalled Their Halogen Work Lights Due to Fire and Shock Hazards